c. Poles supporting cable only (guy below cable). When the guy is below the cable, install
lightning protection wire from the pole top down to a point above the guy mounting hardware. Bend
and drive the ends of the protection wire into the pole. Staple the protection wire as previously
described in paragraph 1a. Install a connecting wire from the square washer of the cable suspension
clamp to the vertical run of the protection wire.
d. Poles with guy-to-strut and strut-to-anchor guys. If the separation between the pole-to-strut
guy and the-
(1) Anchor guy is less than 4 inches (10.16 cm) at the strut, install lightning protection wire
on the strut in the same manner as that described for an anchor-guyed pole in paragraph b above.
(2) Strut-to-anchor guy is more than 4 inches (10.16 cm), install lightning protection wire on
both the pole and the strut in the same manner as that described for an unguyed pole in paragraph 1a.