Observe percent rated current meter.
exceed 5 percent load difference between
phases. An 0.8 power factor load equals a 100
percent meter reading for maximum rated load. A
1.0 power factor load equals an 80 percent
meter reading for maximum rated load.
Adjust speed control
percent rated current for either one-phase 120 V output, one-phase
120/240 V output, or three-phase 120/208 V output.
j. Refer to Table 7 and perform during operation PMCS.
Operation in extreme cold.
a. Use oil IAW TMs and change oil only when its warm.
b. Use arctic grade diesel fuel.
c. Keep batteries well charged and serviced.
d. Ensure air cleaner control is in the cold weather position.
blades should be fully
for cold engine,
under a light load and
more as the load
f. Hold master switch in the start position for 2 minutes after
engine reaches operating speed.
Stopping the 5- or 10-kw Diesel Generator Sets.
Refer to Figure 45.
a. Move AC CIRCUIT BREAKER to OFF position.
b. Move MASTER switch to OFF position.
c. For emergency stop, pull DC CONTROL CIRCUIT BREAKER.
d. Refer to Table 7 and perform after operation PMCS.