PMCS FOR 15-KW DIESEL GENERATOR SET (CONTINUED).
Operation of 15-kw diesel generator set.
a. Prepare generator for starting.
(1) Ensure proper load connections.
(2) Close all access doors with the exception of those for the
generator air vent and the control cubicle.
Lock the generator set
air inlet doors in OPEN position.
(4) If the generator set fuel tank is being used, place the
START-RUN-STOP switch in the RUN position and the BATTLE SHORT switch
in the ON position. Check the fuel level gauge for sufficient fuel